The major power outage affecting sections of the territory is as a result of an engine malfunction at the territory’s main power plant on Tortola.
This is according to Permanent Secretary in the Ministry of Works & Utilities, Jeremy Hodge, who said the mechanical issues began approximately 9:35 am.
“Engine number-11 broke a control airline which caused the unit to trip,” Hodge said. “The control air in the system was rapidly depleted as a result; causing engines 11 and 12 to trip as well.”
“Engine-eight was running at the time but could not carry the load so this unit tripped on overload. As a result of these events, the territory suffered a total blackout,” Hodge further explained
The permanent secretary said work to rectify the issue is ongoing, adding that power will return to the affected areas ‘section by section’.
Copyright 2020 BVI News, Media Expressions Limited. All Rights Reserved. This material may not be published, broadcast, rewritten or distributed.